A series of 3 cross-laminated timber (CLT) fire-resistance tests were conducted in accordance with ULC S101 standard as required in the National Building Code of Canada.
The first two tests were 3-ply wall assemblies which were 105 mm thick, one unprotected and the other protected with an intumescent coating, FLAMEBLOC® GS 200, on the exposed surface. The walls were loaded to 295 kN/m (20 250 lb./ft.). The unprotected assembly failed structurally after 32 minutes, and the protected assembly failed after 25 minutes.
The third test consisted of a 175 mm thick 5-ply CLT floor assembly which used wood I-joists, resilient channels, insulation and 15.9 mm ( in.) Type X gypsum board protection. A uniform load of 5.07 kPa (106 lb./ft²) was applied. The floor assembly failed after 138 min due to integrity.